Langley Operations Support Center
Langley Air Force Base
The Langley Operations Support Center currently houses over $500 million in IT equipment serving Air Force operations in different combat theaters worldwide. When the building failed to meet its turn-over deadline because of over 100 roof leaks, Wiley|Wilson identified roof leaks were a result of negative building pressure, which had also resulted in a collapsed air hander mixed air wall.
The team revised the sequence of operations and added three static pressure sensors to resolve the problem. Within two days, only two roof leaks remained and the system operated using less energy than before the modifications.